IEC 60067-19 explained
Dr Martin Killeen outlines the requirements of the international Repair, Overhaul and Reclamation of Hazardous Area Equipment standard IEC 60079-19, and highlights how it impacts both service providers and end users.
IEC 60079 is a series of explosive atmosphere standards that covers an array of considerations for component use in hazardous areas, as well as defining different hazardous area classifications. An important section of the series specifically covers equipment repair, overhaul, reclamation and modification. This is distinct from the maintenance of equipment, other than when repair and overhaul cannot be separated from maintenance.
In 1984, AEMT and BEAMA jointly produced a code of practice for the repair of Ex rated equipment, and in 1993 this was first adopted as a British standard and published as BS EN 60079 Part 19.
The standard was internationalised in 2004 and published as IEC 60079-19, with additional requirements during overhaul and repair of Ex equipment. The updated standard removed the exclusion of mining and introduced all explosive atmospheres - including dusts. It also introduced new requirements for competency of persons, and when it comes to liability in the event of an explosion, those last requirements serve to define responsibility.
Those parties charged with buying-in overhaul and repair services, and signing them off, along with those companies who are offering the services, also need to be aware that IEC 60079-19 was significantly updated again in 2011, with a subsequent amendment in 2015, with the inclusion of specific Group I requirements and the inclusion of offshore requirements.
IEC 60079-19 lays down the general principles of repair, overhaul, reclamation, alteration and modification that are common to all explosion-protected equipment, with additional clauses to provide instructions relevant to specific types of protection.
Assuming that repairs and overhauls are carried out using good engineering practices, then the finished equipment is considered as being conformant to the original standard the manufacturer’s specification. Where this specification data is not available, then equipment can be described simply as having been repaired in conformance to IEC 60079-19 and meeting the relevant standard the equipment was designed to meet. Steps taken to obtain the original specification data should be documented.
All repair or overhaul work carried out must be fully documented, and job reports submitted to the user. Repair facility records should be maintained to provide a complete audit trail of the work carried out and all of the steps taken, including measurements such as flame path or radial gap compliance. Equipment returned to the end user should be clearly labelled as having been repaired or overhauled, with the relevant manufacturing standards it meets, and the repairer identified.
Where reclamation is being carried out, this should be performed by competent personnel. Ultimate responsibility falls under the repair facility, even if reclamation work is out-sourced to a third-party. Not all procedures are applicable to all types of protection and IEC 60079-19 gives instructions on what can and cannot be reclaimed. Where equipment is to be modified rather than repaired, then alterations need to be specifically permitted in the certificate documentation, or, if that documentation is not available, then the proposed alteration needs to be confirmed by the manufacturer, in writing, to be permitted by the certificate.
If a modification means that the equipment can no longer be confirmed as meeting the original certified specification, then the user needs to be notified in writing, with a report stating that the equipment cannot be used in an explosive atmosphere without additional assessment.
Temporary repairs to achieve continued short-term operation of equipment can only be carried out if it can be demonstrated that explosion-protection capabilities are maintained or if other appropriate explosion-protection measures are taken. Any temporary repair should be brought up to full repair standards as soon as possible.
A key section of the standard details additional requirements for the repair and overhaul of equipment that is Ex d rated. The standard focuses on requirements for enclosures, cable and conduit entries, terminations, insulation, internal connections and windings. Detailed instructions are also given on a number of testing processes for windings after any repair.
There are a host of additional requirements for flameproof brakes, other auxiliary devices, light-transmitting parts, encapsulated parts, batteries, lamps, lampholders, ballasts and breathing devices.
The standard details additional requirements for the repair and overhaul of equipment rated as intrinsically safe (IS). This focuses on equipment such as enclosures, cable glands, terminations, soldered connections, fuses, relays, shunt diode safety barriers, PCBs, optocouplers, electrical components, batteries, internal wiring, transformers, encapsulated components, and non-electrical parts.
Not all of these parts can be repaired, and should simply be replaced. Where equipment is repaired or overhauled, the work should be followed by testing of the dielectric strength of the insulation between the intrinsically safe circuit and the metallic enclosure.
No attempt at reclamation should be made on components on which intrinsic safety depends, and any modification of equipment needs to be considered as modification to the complete system from that shown in the IS documentation, and a reassessment should be carried out by a qualified third party – specifically, then, not the company which made the modification.
Another clause within the standard details requirements for the repair and overhaul of pressurised equipment. While it is preferable to obtain new parts from the manufacturer, in principle damaged parts such as enclosures can be repaired or replaced. Detailed instructions are provided as to what can and cannot be done with the likes of enclosures, cable and conduit entries, terminations, insulation, internal connections and windings, along with instructions for testing after the repair.
While Ex d, pressurised and intrinsically safe equipment will probably represent the bulk of the most safety-critical repair and overhaul work in hazardous areas. IEC 60079-19 also offers detailed instructions for equipment with protection type ‘e’ (increased safety), type ‘n’, Group III ‘t’ (Dust), and type ‘pd’ (pressurised).
Annex B of the standard defines the knowledge, skills and competencies of ‘responsible persons’ and ‘operatives’. Responsible persons are those responsible for the processes involved in the overhaul, repair and reclamation of the types of explosion protected equipment as defined within the standard. They should confine their involvement to overhaul, repair and reclamation, and should not be involved in modification without expert guidance.
Any repair facility must appoint a ‘responsible person' with the required competencies within the management organisation, to accept responsibility and authority for ensuring that the overhauled/repaired equipment complies with the certification status agreed with the user. That person must have a working knowledge of the appropriate explosion protection standards and an understanding of this standard. This requirement means that it is the responsible person who takes the final decision that Ex Equipment is in compliance and can be returned to the customer.
Operatives, as defined in the standard, who will be working on equipment and who may be taking decisions that would have an impact on the certification status of the Ex equipment, need to work under the surveillance of the responsible person. Other operatives involved in the overhaul and repair processes do not need to be independently assessed as competent to IEC 60079-19 although they need to be aware of requirements.
The service facility of course has a responsibility to demonstrate compliance with the requirements of IEC 60079-19, but importantly there is also an onus on the user to ascertain that the service facility can indeed demonstrate compliance. In the event of any problem with repaired, overhauled or modified equipment, investigation bodies will look for evidence of due diligence from both parties.
Dr Martin Killeen is a technical consultant for the Association of Electrical and Mechanical Trades (AEMT), an international association representing leading companies in the electrical and mechanical service and repair industry.
Source: Control Engineering Europe - All Articles